System for voltage regulation, control protection and monitoring of state of changers under power transformer load, voltage regulators, capacitor banks and similar

ABSTRACT

System for voltage regulation, control, protection and monitoring of state of changers under power transformer load, voltage regulators, capacitor banks and similar”, is preferably applied to power transformers ( 1 ) and voltage regulators and similar, through a microprocessor ( 2 ) it provides innovating functions that make up for deficiencies of currently existing voltage relays, highlighting pre-programming, by means of man-machine interface such as, for example, keyboard and display ( 3 ), or serial communication ( 4 ) of several settings and different voltage regulation parameters, each adequate setting for a certain prevailing load condition, performed by means of dry contact inputs ( 5 ), contact outputs ( 6 ) destined for self-diagnosis signaling and alarms ( 7 ); voltage regulation allows parameter selection to be made by means of daily and hourly programming through an internal clock ( 8 ); said system (S) also has the non-volatile memory function ( 9 ); CDC blocking function ( 10 ) that directly acts on the motorized drive ( 11 ) of the CDC; and maintenance assistant functions of the changer under load ( 10 ).

BRIEF INTRODUCTION

This Invention patent application deals with an unheard of “SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR” remarkably with a voltage regulation system, provided with innovating functions and features that enable making up for deficiencies of currently used voltage relays, by preserving unbiased treatment to consumers, residential or business irrespective of demand curve variations.

BRIEF BACKGROUND

Power transformers and autotransformers and voltage regulators are used in an electric power generation, transmission and distribution system for power transfer, normally changing the output voltage value in relation to input. In order to allow controlling voltage supplied to load, its windings are equipped with taps which are connected to a CDC or OLTC (On-Load Tap Changer), which makes TAP change used with the energized transformer and with connected load, changing the coil ratio and consequently transformer output voltage.

In order to make the change and tap change the CDC has a motorized drive mechanism and regulated by signals received in its inputs, to raise or lower the tap.

STATE OF THE ART

Currently in order to allow automatic voltage regulation supplied to load, transformers are equipped with a device called automatic voltage regulator relay, or voltage relay or simply relay 90, which send to the changer under load signals to lower or raise the tap position, so as to keep voltage in the load within programmed limits in relay parameterization.

In order to perform the automatic voltage regulation function, the voltage relays perform the transformer output voltage measuring through a power transformer (PT) and, the load current through a current transformer (CT). With these measurements, the voltage relay makes calculation of the voltage that actually reaches the load, by taking into consideration voltage drop in the transmission line, proportionate to the load current. Calculated voltage in load is then compared to a set of regulation parameters programmed in the voltage relay in order to determinate when there is need for change in CDC tap. Said parameters include:

Rated voltage in load;

Tolerance margin, which is the allowed voltage percentage over and under rated voltage;

Timing for CDC actuating in order to correct voltage, so as to avoid unnecessary tap change as a result of temporary voltage deviations, in which actuating time can be constant—regardless of the voltage deviation magnitude in relation to programmed tolerance margin (linear timing); or inversely proportional to voltage deviation magnitude in relation to tolerance margin (inverted timing);

Parameters referring to voltage drop in line in a given load current condition (rated current), allowing the voltage relay to calculate actual voltage reaching the load.

Generally current voltage relays also have an input for making CDC tap position measurement, through a position sensor existing in it. Measured tap position is then indicated to operator who may also perform CDC command in manual manner, by blocking automatic voltage regulation commands. Based on this CDC tap position measurements, some existing voltage relays also perform CDC control in transformers electrically connected in parallel, therefore using the concept called Master-Command or Master-Follower. In this concept, one of the transformers in parallel is selected in master mode and the other in commanded mode. Every tap change performed by the master must be repeated by followers that lose their command independence to simply obey master transformer tap changes. In this way, all transformers will be in the same tap position, which prevents current circulation among windings in parallel, sending new trap change commands is blocked, preventing tap difference between transformers from increasing. 14) In operation in parallel of transformer banks consisting of individual single-phase transformers, additional care must be taken in order to ensure that the three single-phase transformers of which a bank consists are with their CDCs in the same tap position, in order to prevent a voltage unbalance between the three-phase system phases. To this end a synchronism, check is performed between tap positions of the three single-phase transformers of the same bank, blocking CDC operation and issuing an alarm is any tap discrepancy occurs between the bank phases. For maintenance and testing purposes only, when the bank is not electrically connected in parallel to others, is when CDCs of each phase can be operated in different tap positions. In order to allow these tests and maintenances in existing system will have a selection, manually performed by the operator, where it is indicated whether the three transformers of the same bank must operate in the same tap position (“bank” mode) or in individual manner (“individual phase” mode).

STATE OF THE ART DISADVANTAGES

-   -   One of the limitations of existing voltage relays is related to         transformers serving consumers in different load profiles, such         as residential, business and industrial consumers. In these         cases there may be prevalence of a certain type of consumer on         certain weekdays or times and, of another type of consumer in         other periods of the week. In this way, ideal parameter settings         for a type of consumer may be totally unsuitable for another         type of consumer. With currently available voltage relays there         is no satisfactory solution for this occurrence, forcing the         operator to favor a certain type of consumer in detriment of         another or, then make periodic manual changes to the voltage         relay parameter settings.     -   In conventional voltage relays used in transformers, one of the         programmed parameters for making the voltage regulation is to         delay CDC operation in order to correct voltage that, has as a         function preventing unnecessary tap changes is important due to         the fact that the CDC is the equipment that generates the         highest maintenance costs in transformers and, the need for         maintenance in the CD is basically determined by the number of         trap changes made. Accordingly, in order to reduce the changer         maintenance costs the ideal is to make the highest possible         timing adjustment. On the other hand, maximum times that loads         may remain in voltages over or below tolerance limits are often         determined by the electric sector regulatory agencies that, may         establish different times for voltage below or over tolerance.         In this context, conventional voltage relays are fitted with a         single timing adjustment used both when there is need to         increase voltage and when it is necessary to decrease voltage.         This fact forces the operator to adjust timing according to the         shortest time defined by regulatory agencies (between allowed         times for a voltage below or over tolerance), which results in         additional CDC actuations in a condition that a longer operation         time would be allowed.     -   In currently used voltage relays in transformers, when voltage         in the lead exceeds lower and upper limits defined by programmed         tolerance margin timing count is started for CDC operation. Said         timing may be a linear type, in which actuation time is         constant, regardless of the voltage deviation magnitude in         relation to programmed tolerance margin, or reverse type timing,         in which actuation time is inversely proportional to voltage         deviation magnitude in relation to the tolerance margin. As         already mentioned, timing settings are based on maximum times in         which loads may remain with voltages over or below tolerance         limits, and said times are often determined by the electric         sector regulatory agencies, which, generally, determine shorter         times as voltage deviation increases over or below allowed         tolerance limit. Accordingly, conventional relays have as the         only feature meeting the needs of shorter timings for higher         voltage deviations than reverse timing. This forces the operator         to adjust timing in order to meet or exceed arbitrarily defined         times by the regulatory agency, which usually tends to cause         unnecessary additional CDC actuations when adjustment made takes         a shorter actuation time than required by the regulatory agency.     -   On-Load Tap Changers (CDC) are equipped with a motorized drive         mechanism that receives command signals to increase or decrease         the tap position. Such drive has intern ally several control         elements, such as, relays, mechanically driven end of line         switches, among so many other elements. Certain failures in         referred control elements can lead the CDC to make unsolicited         tap changes, which may be repeated in successive manner leading         the CDC to reach an extreme upper or lower position, causing         either too high or too voltage values in the load. The         occurrence of this type of occurrence is highly undesirable by         consequences that may be, for example, load shutoff by its         protection actuation or even damages in loads.     -   Following the same above-mentioned context, of the Changers         (CDCs) motorized drive mechanism, certain failures may lead the         CDC not to make requested tap changes by the voltage regulation         system, which may lead voltage in the load to slowly vary as         load current and primary voltage in transformer are changed.         After some time, voltage in load may reach very high or very low         due to lack of voltage correction that would be provided by CDC         operation, with consequences that may go from load shutoff by         actuation of its protections or even damages in load.         Accordingly, in conventional relays, inoperative CDC condition         is only perceived after some time, when voltage reaches too high         or too values, already with damage to the load.     -   Several researches conducted around the world referring to         failures and stoppages for maintenance in transforms clearly         signal that the CDC is the equipment that generates the highest         failures rates and maintenance costs in transformers, the need         for maintenance in the CDC being basically determined by the         number of tap changes made by it. Currently, CDCs are equipped         with mechanical operation counters that record the number of tap         changes made since the equipment operation start, control of         this number of operations being made by maintenance personnel,         which in a certain frequency moves to the CDC and writes down         the number of operations at that time. With this information         inspection and/or maintenance need is determined in the CDC,         having as a parameter the number of operations since the last         inspection/maintenance if the value recommended by manufacturer         is reached.     -   Following above-commented research, in relation to CDCs, the         need for maintenance in the latter is also determined by the         wear and tear of contacts that make electric arc interruption         during tap change. As is known by technicians in the matter, the         wear of said contacts is proportional to the sum of interrupted         current squares. Currently, maintenance in CDCs is focused on         their number of operations, which opens the possibility of         problems appearing in CDCs, if interrupted currents by their         contacts have sufficient intensity to cause excessive contact         wear, anticipating the number of operations predicted for         maintenance. Additionally, maintenances simply based on CDC         operations, statistically reveal that maintenance could have         been postponed for some time, taking into account that changer         contacts are found in good state.     -   In conventional relays in which operations control is done in         parallel of transformers by the Master-Commanded method it is         necessary to select for each transformer its function in master         parallelism control, commanded or further individual (if         transformer is not operating in parallel with any other). Bu the         Master-Commanded concept, only one of transformers can be         selected as master and there may not be transformers selected as         Commanded if there is no Master transformer. This enables making         invalid configurations for parallelism control in existing         voltage relays, such as, for example, the selection of more than         one transformer as master or selection of transformers as         commanded without the existence of a master.     -   In existing voltage relays where operation control is made in         parallel of transformers by the Master-Commanded method, the         voltage relay makes synchronism verification taps of         transformers in parallel, blocking CDC operation and issuing an         alarm if there is tap discrepancy. However, in the condition in         which transformers are not in parallel and, therefore are         selected for operating in individual mode, there is no         obligation for their tap positions to be equal. However, at any         time it may be necessary for said transformers having to be         operated in parallel and, to this end of them will have to be         selected as mater and the others as commanded. It may occur that         master-commanded selections will be made with transformer CDCs         in different tap positions, which will lead the voltage relay to         issue a tap discrepancy alarm between CDCs.     -   For two or more transformers to be electrically connected in         parallel it is necessary for their CDCs to be in the same tap         position, so as to prevent current circulation among windings.         Establishing the electric connection of transformer windings in         parallel is usually done by closing a substation circuit breaker         that can only be closed after transformer CDCs are in the same         tap position. Currently this verification is manually made by         the operator, therefore, being subject to human failure.     -   In conventional relays where operation control in parallel of         transformer banks consisting of single-phase transformers is         done, it is necessary to ensure, during normal operation, that         the three single-phase transformers of which a bank consists are         with their CDCs in the same tap position. However, in order to         allow testing and maintenances existing systems have a selection         where it is indicated whether the three transformers of the same         bank should operate in the same tap position (“bank” mode) or in         individual manner (“individual phase” mode). This selection is         made manually, which opens the possibility for an operator         error, which may select the transformer CDC of each phase to         operate in individual manner, and consequently in different tap         position from the other phases, even if the transformer bank is         in normal operation electrically connected in parallel to other         banks.     -   In existing systems where operation control in parallel of         transformer banks consisting of single-phase transformers is         done, a synchronism checking is made between tap positions of         the three single-phase transformers of the same bank, blocking         CDC operation and issuing an alarm if a tap discrepancy occurs         between the bank phases. However, in the condition that the bank         is in maintenance and its phases are in “individual phase” mode,         there is no obligation for their tap positions to be equal. At         any time, however, it may be required for the bank to return to         operate normally, and to this end the phases should be changed         to “bank” mode. This opens the possibility for phase selections         to “bank:” mode to be made with the three phases of transformers         in different tap positions, which will lead voltage relay to         issue a tap discrepancy alarm between CDCs.

THE NEW INVENTION

Thinking about the above-commented inconveniences, the inventor, a person working in the electric power sector, has created the system in question that comes to make more reliable voltage regulation, protection and state if changers under equipment load state monitoring, such as, power transformers and voltage regulators, making up for deficiencies of current relays that perform voltage regulation based on a single set of parameters; the other way about, proposed invention provides pre-programming for different voltage regulation parameter settings, each setting being suitable to a given prevailing load condition, allowing consumer service with different load profiles, having to this end several regulation parameters, adjustable in independent manner.

Furthermore, the proposed system allows selection of the voltage regulation parameter set made by dry contacts where a combination of open and closed contacts is used indicative of the parameter set that must be used in voltage regulation. In continuity, the claimed system allows voltage regulation parameter set selection to be made by daily and hourly programming, in addition to other temporary parameters. Another innovation of the proposed system is the possibility of independent value adjustment of CDC actuation timing for conditions in which voltage is over or below allowed tolerance margins. Proposed system also allows adjustment of several voltage deviation ranges, different CDC actuation times being associated with each deviation range. The system also has a mass memory function (non-volatile), where measurement values made by the system are recorded obeying the interval programmed by the operator, having several innovating features. In conformity with the new invention it is possible to block the erroneously tripped CDC, equally with several features to be discussed later. Such as mentioned above the system has the function of detecting the inoperative CDC, before voltage reaches extreme values also meeting several features. In this same line, the system proposed herein has the innovating function of CDC maintenance assistant, with several features oriented toward statistical maintenance control of changers under load. Another new system function is the “Master-Commanded-Individual” smart selection programming, when there is an operation in parallel of several transformers, and “Bank-Individual Phase” smart programming, when using banks consisting of three independent single-phase transformers, preventing several inconveniences of existing systems. At last the proposed system has the synchronism signaling function and correct programming, which automates the tap synchronism checking process when electrically connecting transformers in parallel, which prevents human failures in this checking.

ADVANTAGES OF THE NEW INVENTION

It prevents, in proposed voltage regulation system parameterization, the operator from being forced to privilege a certain consumer in detriment of others or then having to make periodical manual changes to voltage relay parameter settings.

Allow that, by means of dry contacts, it will be possible to select a set of voltage regulation parameters, at a distance, by using, for example, selection switches within operator reach in the control room or further output contacts of remote terminal units (RTUs);

By the selection of voltage regulation parameter set through daily and hourly programming, allow the operator to program the voltage regulation system to automatically adapt it to prevailing conditions of load profiles subject to hourly, daily and weekly variations.

By timing setting programming for independent CDC actuation in the event that voltage is over or below allowed tolerance margins, giving conditions for meeting the regulatory agency requirements in relation to allowed times for voltage off tolerance, at the same time as reducing to the maximum possible the number of CDC operations, reducing maintenance costs.

By programming settings for several voltage deviation ranges, each associated deviation range being different CDC actuation times (one time adjustment to increase voltage and one adjustment to reduce voltage), conditions are given for the user to create a customized timing mode, in which operation time diminishes exactly as desired as voltage deviation increases, so as to exactly meet the regulatory agency requirements in relation to allowed times for voltage off tolerance, at the same time as reducing to the maximum possible the number of CDC operations, reducing maintenance costs.

By the mass memory function, allows the operator to choose for recording in the memory only variables he considers important, avoiding spending memory space with unnecessary variables for their application.

Still by the mass memory function, the operator may choose to record not only the variable instantaneous value, but also minimum, maximum, arithmetic mean or square variable mean values during the time interval since the last made recording. With that it becomes possible to retrieve, from data in memory, the electric system behavior (for example, maximum, minimum, average voltages, etc.) and analyze tension regulation efficiency.

By the tripped CDC blocking function, preventing the occurrence of serious undervoltages or overvoltages that may cause forced transformer switching off or damage to loads connected to it.

-   -   By the “CDC maintenance assistant” function, it allows:         Automating CDC control and number of operations, reducing costs         related to traveling to the equipment just to check the current         number of operations in mechanical command;         Better maintenance manpower utilization, which avoids spending         time manually controlling CDC maintenance intervals, with         consequent cost reduction;         CDC maintenance lack risk reduction due to human failures in         maintenance interval control;         With the maintenance warning issued in advance by the voltage         regulation system, better interval adjustment between         inspections and/or maintenances occurs, avoiding excessive         delays in maintenances caused by lack of logistics preparation         for jobs;         Working in conjunction, the several above-listed benefits may         allow failures rate reduction in CDCs, due to interval         adjustment and CDC maintenance quality improvement, taking into         consideration that maintenance personnel have their time freed         for better preparation for the activity.

Still by the “CDC maintenance assistant function, it allows:

Making the CDC maintenance philosophy transition of maintenance based on time for maintenance modeled on the state of the equipment, avoiding unnecessary CDC interventions and, consequently, reducing maintenance costs; CDC failure risk reduction due to excessive wear of arc interruption contacts; In order to prevent unnecessary CDC interventions, it reduces the risk of problems caused in it by human failures when intervening for maintenance; With the maintenance warning issued in advance by the voltage regulation system, maintenances can be prepared in advance to become effective at the ideal time only, preventing excessive delays in maintenances caused by lack of materials and/or lack of logistics preparation for jobs; Working in conjunction, the several above-listed benefits may allow failures rate reduction in CDCs, due to knowing the actual state of arc interruption contacts. Furthermore, it improves CDC maintenance quality, since when preventing unnecessary interventions in CDC, maintenance professionals have their time freed for better preparation for the activity.

By the smart master-commanded-individual programming, all possibilities for the operator making invalid programming are inhibited, such as more than one transformer as a master, or the existence of commanded transformers without there being a master, or further selecting a transformer as commanded without its tap position being equal to the mater, among other invalid programming possibilities.

By smart “individual bank-phase” programming, possibilities for the operator making invalid programming are inhibited, such as selecting that the transformer CDC of each phase will operate in individual manner, and consequently in different tap position from the other phases, even if the that transformer bank is in normal operation and electrically connected in parallel to other banks, among other invalid programming possibilities.

By the “correct synchronism and programming signaling” function”, preventing the operator from making the mistake of electrically connecting in parallel transformers that are not found in the same tap position.

Next, the invention will be technically explained, by using as a basis block diagrams.

DETAILED DESCRIPTION

The “SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR”, covered by this Invention patent application, preferably applies to power transformers (1) and voltage regulators and similar, it being that this system (S) hereinafter referred to as voltage regulation system, by means of a microprocessor (2) provides innovating functions that make up for deficiencies of currently existing voltage relays, highlighting pre-programming, by means of man-machine interface such as, for example, keyboard and display (3), or serial communication (4) of several settings and different voltage regulation parameters, each adequate setting for a certain prevailing load condition, performed by means of dry contact inputs (5), contact outputs (6) being destined for self-diagnosis signaling and alarms (7). Voltage regulation allows parameter selection to be made by means of daily and hourly programming through an internal clock (8). Said system (S) also has the non-volatile memory function (9); CDC blocking function (10) that directly acts on the motorized drive (11) of the CDC; tap position measurement (12) with inoperative CDC detection or release, CDC maintenance assistant; smart programming and correct synchronism and correct programming function (7).

As already commented, transformers (1) are used in electric power generation, transmission and distribution, usually changing the output voltage value for load (13) in relation to input voltage (14). This is done with windings equipped with taps connected to an Onload Tap Changer (CDC) (15) that makes tap change with the energized transformer (1) and connected load. Therefore the CDC has a motorized drive mechanism (11) that obeys input signals to raise and lower the tap (10), In order to perform the voltage regulation function, an output voltage measurement is made (17) by means of a power (PT) and current transformer (17′) of load by means of a current transformer (CT), more particularly, proposed regulation system (S) consists of a microprocessor (2) that with said voltage and current measurements (17 and 17′) provides new functions and features, making up for deficiencies of currently existing relays that make voltage regulation base on a single parameter set; unlike the applied for system (S) that allows them to be pre-programmed by a man-machine interface such as, for example a keyboard and display (3), or a serial communication (4) several settings for voltage regulation parameters, each setting being adequate for a given prevailing load condition that may be identified by the time informed by the internal clock (8). In order to enable this function, the system (S) proposed herein has six or more regulation parameter sets adjustable in independent manner, each set having the parameters described below:

Desired rated voltage in load;

Voltage variance percentage allowed over and below rated voltage;

Timing adjustment for CDC actuation in order to correct voltage;

Choice of linear or reverse timing type;

Parameters referring to voltage drops in the line;

As already mentioned, the voltage regulation system allows selection of the voltage regulation parameter set used in the system operation to be made by means of daily and hourly programming, consisting of the weekdays and time ranges for activating parameter set. For each parameters weekdays (Sunday through Saturday) are selected, in addition to the time range defined by start hour, minute and second, range end hour, minute and second. Within the days and time range selected for a given set it will be used for voltage regulation. In other words, based on its real-time internal clock (8) that keeps day, month, year, weekday, hour, minute and second information and based on performed daily and hourly programming the voltage regulation system makes the choice of the regulation set to be used at current time.

In addition to regulation parameter set selection through a daily/hourly programming, this selection can be made by dry contact input (5). The combination of open and closed contacts in these inputs indicates to the voltage regulation system which parameter set must be used. The combination of open and closed contacts in these inputs can be encoded in decimal manner, that is, each parameter set directly corresponds to an input contact, or can be encoded in binary manner, with the combination of input contact states forming a number corresponding to the respective parameter set.

The proposed voltage regulation system allows independent CDC timing and performance values to be adjusted for conditions in which voltage is over or below allowed tolerance margins, providing conditions for meeting the sector regulatory agency requirements in relation to allowed times for voltage off tolerance, at the same time as CDC operation time is reduced to the maximum possible, reducing maintenance costs.

Another proposed system innovation is the adjustment, in addition to the tolerance margin, of several voltage deviation ranges, it being that each deviation range is associated with different CDC operation times (for each deviation range one time setting for increasing voltage and one setting for reducing voltage).

Such a fact allows the operator to create a customized timing mode, in which operation time diminishes exactly as desired as voltage deviation increases, so as to exactly meet the regulatory agency requirements in relation to allowed times for voltage off tolerance, at the same time as CDC operation time is reduced to the maximum possible, reducing maintenance costs.

The regulation system proposed herein The system also has the mass memory function, where they are recorded in a non-volatile memory (9), obeying the interval programmed by the operator, measurement values made by the system, it being that this function has the following features:

Variables to be recorded can be freely chosen by the operator among all measures or calculated values by the system, such as, measured voltage in transformer, voltage in load, load current, powers, frequency, power factor, CDC tap position, etc.

For each variable selected for recording by the operator the recording mode can be chosen among the options: instant value (measured value at recording time), arithmetic mean of measurements made since the last recording in memory, square mean of measurements made since the last recording in memory or minimum value of measurements made since the last recording in memory.

One and the same measurement can be selected for recording in memory in several different modes. For example, “voltage in load” variable can be selected for recording with instant value, mean value, maximum value and also minimum value.

In order to prevent certain failures in CDCs the proposed voltage regulation system has the “tripped CDC blocking” function, with the following features:

Performance by the voltage regulation system of CDC tap position measurement (12);

It considers normal CDC operation the condition in which the voltage regulation system issues a signal to the CDC to raise or lower tap position (10) and after that the CDC tap position undergoes a change in the same direction of sent signal (raise or lower the tap);

It considers that the CDC is tripped if a change in measured CDC tap (12) occurs without the voltage regulation system having previously sent a signal (10) requesting this change, or further if the voltage regulation system issues a signal for tap change (10) and the CDC makes a change in the opposite direction to issued signal. In this case an output contact (6) can be programmed by the operator for remote signaling (7) of the occurrence;

In order to prevent false tripped CDC alarms, due, for example, to tap changes manually requested by the operator directly on the motorized drive panel, it may be programmed in the voltage regulation system to only consider that the CDC is tripped if several successive tap changes occur, being the number of tap changes for considering that the CDC is tripped programmed by the operator;

A tripped CDC situation is detected, as described above, an output contact (10) is activated in the voltage regulation system. This contact can be connected by the operator in order to switch off the CDC drive motor supply (11), forcing him in this manner to stop tap changes and avoid the consequences such as forced transformer switching off or damage to the load.

In order to allow quick detection of an inoperative changer, before voltage reaches too high or two low values, the voltage regulation system proposed herein has the “Inoperative CDC detection” function with the following features:

Performance by the voltage regulation system of CDC tap position measurement (12);

It considers that the CDC is found in normal condition if the voltage regulation system issues a signal (10) to the CDC to raise or lower tap position and after that the CDC tap position undergoes a change in the same direction of sent signal (raise or lower the tap, detected by the CDC position measurement) within the time period programmed by the operator;

It considers that the CDC is inoperative if the voltage regulation system issues a signal (10) to the CDC to raise or lower tap position and, after that the CDC tap position does not undergo a change within the time period programmed by the operator (the change is detected by measuring the CDC position);

In order to avoid false inoperative CDC alarms, such as, for example, during maintenances in which the CDC is kept inoperative, the operator may enable or disable this function in the voltage regulation system;

When detecting the inoperative CDC situation, as described above, the condition is signaled through an alarm indication in the voltage regulation system that, may also activate an output contact (6) for remote alarm indication (7);

The alarm indication will remain active in the voltage regulation system and the alarm contact will remain activated until the operator makes a manual alarm reset informing to the system voltage regulation system that he is already aware of the problem.

The operator may also enable the voltage regulation system to make an automatic inoperative CDC alarm reset, the automatic reset being made as soon as new CDC tap change attempt is successively made.

A new function of the proposed voltage regulation system is of CDC Maintenance Assistant, with the following features:

Total CDC operation number count, since the beginning of its operation, by measuring the CDC position (12). Every time the measured tap position changes the CDC operation counter increases the number of required operations for making referred tap change (one operation in most cases, there may also be several operations in case of CDCs with intermediate positions);

Partial CDC operation number count since the last inspection or maintenance made by the operator, by measuring the CDC position (12), in similar manner to above-described total operation number count;

Initial operation numbers of both counters (total and partial) adjustable by the operator, allowing utilization of the CDC, also in old equipment, in addition to allowing operation count correction in the event of a failure in the voltage regulation system.

A warning indicating that the operation number for CDC maintenance when partial operation count (since the last maintenance) has exceeded the number of operations for maintenance adjusted by the operator; with the possibility of programming an output relay (6) for remote signaling (7);

CDC average daily operation count, made by dividing the sum of total operation number in the last X days by the number of X days, X being a time window programmable by the operator between one and three hundred and sixty five days;

Approximate Y remaining time calculation for reaching the number of operations for maintenance, according to the ratio below:

$Y = \frac{\begin{matrix} {\left( {{{No}.\mspace{14mu} {of}}\mspace{14mu} {operations}\mspace{14mu} {for}\mspace{14mu} {maintenance}} \right) -} \\ \left( {{partial}\mspace{14mu} {operation}\mspace{14mu} {counter}} \right) \end{matrix}}{{Average}\mspace{14mu} {daily}\mspace{14mu} {operations}}$

Warning indication that the number of operations for CDC maintenance will be reached within Y days, when remaining time calculation for Y maintenance is lower than the number of advance days for maintenance warning adjusted by the operator between zero and three hundred and sixty five days, with the possibility of programming an output relay (6) for remote signaling (7);

The maintenance warning indication will remain active in the voltage regulation system and the alarm contact(s) will remain activated until the operator makes a manual warning reset, informing the voltage regulation system that maintenance has already been performed. Once the reset is made, partial operation count since the last maintenance is zeroed and warnings are switched off for maintenance.

In addition to the above-listed the “CDC maintenance assistant”, has further the following features:

Every time a CDC tap change is made, detected by the tap measurement means (12), the voltage regulation system the load current measurement (17′) at the time of tap change and raises it to the power of 2. Obtained value is added to the already existing one in the total changed current sum recorder since the beginning of the CDC operation, which is kept in a non-volatile memory in the voltage regulation system;

As described above, every time a CDC tap change is made, detected by means of tap measurement (12), the voltage regulation system takes the load current measurement (17′) at the time of the change and raises it to square. Obtained value is also added to the already existing value in another recorder, this one dedicated to the sum of partial change current since the last CDC maintenance, which is kept in the voltage regulation system non-volatile memory;

Initial values of both changed current sum records (total and partial) adjustable by the operator, allowing using the CDC maintenance assistant also in old equipment, in addition to allowing sum corrections in the event of a failure in the voltage regulation system;

A warning indication that the changed current sum for CDC maintenance has been reached when the partial sum record (since the last maintenance) exceeds the sum value for maintenance adjusted by the user, with the possibility of output relay (5 e) programming for remote signaling (7);

Daily increment average calculation in the current sum changed by the CDC, made by dividing the increment in the current sum in the last W days by W number of days, W being a time window programmable by the operator between one and three hundred and sixty five days;

Approximate remaining time Z calculation for reaching sum value for maintenance, according to the formula:

$Z = \frac{\left( {{Sum}\mspace{14mu} {value}\mspace{14mu} {for}\mspace{14mu} {maintenance}} \right) - \left( {{partial}\mspace{14mu} {sum}\mspace{14mu} {recorder}} \right)}{{Daily}\mspace{14mu} {increment}\mspace{14mu} {average}\mspace{14mu} {in}\mspace{14mu} {sum}}$

A warning indication that the number of operations for CDC maintenance will be reached within Z days, when remaining time for maintenance Z calculation is lower than the number of advance days for maintenance warning adjusted by user between zero and three hundred and sixty five days, having the possibility of programming the output relay (6) for remote signaling (7);

The maintenance warning indication remains active in the voltage regulation system and alarm contact(s) will remain activated until user makes manual warning reset, informing the voltage regulation system that maintenance has already been performed, Once this reset is made, the partial sum recorder of changed currents since the last maintenance is zeroed and maintenance warnings are switched off.

Proposed system also performs the “smart master-commanded-individual programming” function, with the following features:

Inhibiting the possibility of selecting any transformer as master if there is already any other transformer selected as master. In this event in which there is already a selected master, all other transformers can only be selected as commanded or individual;

Inhibiting the possibility of selecting any transformer as commanded if there is not yet a transformer selected as master. In this event, in which there is not yet a selected master, all other transformers can only be selected as master or individual;

Inhibiting the possibility of changing the programming of the transformer selected as master to commanded or individual if there is one or more transformers selected as commanded, in the way avoiding that there will be transformers in commanded without there being a master.

In addition to what has already been commented above, the “smart master-commanded-individual programming” function has as features, in addition to those already mentioned:

Rejecting the selection change of any transformer from individual mode to commanded mode if its measured tap position (12) is not equal to a master transformer one, avoiding thereby unnecessary alarm issuing due to tap discrepancy;

If it is insisted in the attempt to program a transformer as commanded without its measured tap position (12) being equal to a master transformer one, in addition to rejecting this programming the voltage regulation system will issue an “invalid parallelism programming” alarm, warning the operator about the situation, with output relay programming possibility (6) for remote signaling (7);

Proposed system also performs the “smart bank-individual phase programming” function, with the following features:

Inhibiting the possibility of selecting any phase of a single-phase transformer bank for operation in the “individual phase” mode if the bank is selected for operation in parallel with other banks, that is, if the bank is selected in master or commanded mode.

Inhibiting the possibility of selecting any phase of a single-phase transformer bank for operation in the “individual phase” mode if the bank is selected for operation in automatic mode, that is, with CDCs being controlled according to load voltage and current measurements.

Only allowing selecting one of the phases of a single-phase transformer bank for operation in “individual phase” mode if the bank is selected for operation in individual and manual mode.

Automatically changing any phase of a single-phase transformer bank that is selected for operation in “individual phase” mode to “bank” mode if the bank is selected for operation in master, commanded or automatic mode.

In addition to what has already been commented above, the “smart bank-individual phase programming” function has as features, in addition to those already mentioned:

Rejecting the selection change of any phase of a transformer from “individual phase” mode to “bank” mode if its tap position is not equal to phase A one, adopted as a reference, avoiding thereby unnecessary alarm issuing due to tap discrepancy. If it is insisted in the attempt to program a phase in the “bank” mode transformer without its tap position being equal to phase A one, in addition to rejecting this programming the voltage regulation system will issue an “invalid parallelism programming” alarm, warning the operator about the situation;

Proposed system also performs the “correct synchronism and programming signaling” function, with the following features:

In transformers selected in individual mode no correct synchronism and programming signaling is issued (since there is no, in this case, commitment to keep tap position equal to master transformer position);

In each transformer selected in commanded mode it is signaled that synchronism and programming are correct only if transformer tap position (12) is equal to master tap position and if current individual master-commanded situation is valid (there is only one master transformer);

In selected transformer is master mode it is always signaled that synchronism and programming are correct, because tap position of this transformer as taken as a reference for selected transformers as commanded and is considered correct by default.

The main usefulness of the above-mentioned function, with above-described features is to serve as a permission signal for closing the circuit breaker that connects the winding of each transformer in parallel with the other, allowing automating the synchronism check function before connection in parallel, which is currently done in manual manner. To that end, correct synchronism and programming signaling can be made by means of a serial communication network (4) or further by activating an output contact (6) for each transformer. 

1. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, preferably applies to power transformers (1) and voltage regulators and similar, used in electric power generation, transmission and distribution systems, usually changing the load output voltage value (13) in relation to input voltage (14), with windings equipped with taps (15), connected to an Onload Tap Changer (CDC) that makes tap change with energized transformer (T) and connected load, to that end the CDC has a motorized drive mechanism (M) that obeys input signals to raise and lop the tap (16); to perform the voltage regulator function, output voltage measurement is made (17) by means of a power transformer (PT) and load current (′17) by means of a current transformer (CT), characterized by proposed regulation system (S) consisting of a microprocessor (2) that with said voltage and current measurements (17 and 17′) provides new functions and features, allowing to be programmed by means of a man-machine interface such as, for example, key board and display (3), or serial communication (4) several settings and different voltage regulation parameters, each setting suitable for a given prevailing load condition, performed by means of dry contact inputs (5), output contacts being (6) destined for self-diagnosis and alarm signaling (7); voltage regulation allows parameter selection to be made by means of daily and hourly programming through an internal clock (8); said system (S) also has the non-volatile memory function (9); CDC blocking function (10) that directly acts on CDC motorized drive (12); tap maintenance assistant function, CDC maintenance assistant function; smart programming and correct synchronism and programming signaling function.
 2. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 1 characterized by the regulation system (S) proposed herein having six or more regulation parameter sets adjustable in independent manner, each set having parameters described below: Desired rated voltage in load; Voltage variance percentage allowed over and below rated voltage; Timing adjustment for CDC actuation in order to correct voltage; Choice of linear or reverse timing type; Parameters referring to voltage drops in the line.
 3. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 2 characterized by selecting the voltage regulation parameter set used in system operation to be made by means of dry contact inputs (5).
 4. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 3 characterized by combination of open and closed contacts in these inputs in order to indicate to the voltage regulation system which parameter set is to be used.
 5. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 4 characterized by the combination of open and closed contacts in these inputs being able to be encoded in decimal manner, an input contact directly corresponding to each parameter set.
 6. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 5 characterized by the combination of open and closed contacts in these inputs being able to be encoded in binary manner, with the combination of input contact state forming a number that corresponds to the respective parameter set.
 7. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 6 characterized by the voltage regulation system allowing regulation parameter set selection used in system operation to be made by means of a daily and hourly programming, consisting of weekdays and time ranges for activating each parameter set; for each parameters set weekdays are selected (Sunday-Saturday), in addition to the time range defined by range start hour, minute, and second and end hour, minute and second; within selected days when the set will be used for voltage regulation; based on its real-time internal clock (8) that keeps day, week, month, year, weekday, hour, minute and second information.
 8. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 7 characterized by based on daily and hourly programming made by voltage regulation system making the choice of regulation set to be used at present time.
 9. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 1 characterized by proposed voltage regulation system allowing independent CDC operation timing values to be adjusted for conditions in which voltage is over or below allowed tolerance margins.
 10. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 1 characterized by proposed system allowing, in addition to tolerance margins for onload voltage, programming several CDC voltage deviation ranges (for each deviation arrange one time setting is programmed for increasing voltage and one setting for reducing voltage).
 11. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 10 characterized by allowing a customized timing mode, in which operation timer decreases precisely as desired as voltage deviation increases.
 12. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 1 characterized by regulation system proposed herein having a mass memory function, in which measurement values made by the system are recorded in non-volatile memory (9) obeying the programmed interval by the operator.
 13. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 12 characterized by the function having features: variables to be recorded may be freely chosen by the operator among all measured or calculated variables by the system, such as measured voltage in transformer, onload voltage, load current, powers, frequency, power factor, CDC tap position; for each selected variable for recording by user, recording mode may be chosen among the options: instantaneous value (measured value at recording time), arithmetic mean of measurements made since the last recording in memory, quadratic mean of measurements made since the last recording in memory, maximum amount of measurements since the last recording in memory or minimum value of measurements made since the last recording in memory; the same measurement can be selected for recording in memory in several different modes, for example, the “onload voltage” variable may be selected for recording with instantaneous value, mean value, maximum value and also minimum value.
 14. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 1 characterized by preventing certain failures in CDCs proposed voltage regulation system having the “CDC blocking” function.
 15. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 14 characterized by the tripped CDC blocking function, based on measuring CDC tap position, having the following features: It considers normal CDC operation the condition in which the voltage regulation system issues a signal to the CDC to raise or lower tap position and after that the CDC tap position undergoes a change in the same direction of sent signal (raise or lower the tap); It considers that the CDC is tripped if a change in measured CDC tap occurs without the voltage regulation system having previously sent a signal requesting this change, or further if the voltage regulation system issues a signal for tap change and the CDC makes a change in the opposite direction to issued signal; In order to prevent false tripped CDC alarms, due, for example, to tap changes manually requested by the operator directly on the motorized drive panel, it may be programmed in the voltage regulation system to only consider that the CDC is tripped if several successive tap changes occur, being the number of tap changes for considering that the CDC is tripped programmed by the operator; When a tripped CDC situation is detected, as described above, an output contact is activated in the voltage regulation system; this contact can be connected by the operator in order to switch off the CDC drive motor supply, forcing him in this manner to stop tap changes and avoid the consequences such as forced transformer switch off or damage to loads connected to it.
 16. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 1 characterized by in order to allow quick detection of inoperative changer, before voltage reaches too high or too low values, the voltage regulation system proposed herein has the “inoperative CDC detection” function”.
 17. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 16 characterized by characterized by the following features: It is considered that CDC is found in normal condition if the voltage regulation system issues a signal to the CDC to raise or lower tap position and after that the CDC tap position undergoes a change in the same direction as sent signal (raise or lower the tap, detected by measuring CDC position) within the time period programmed by the operator; It is considered that the CDC is inoperative if the voltage regulation system sends a signal to the CDC to raise or lower tap position, and after that CDC tap position does not undergo a change within the time period programmed by the operator (the change is detected by measuring CDC position); In order to prevent false inoperative CDC alarms, such as, for example, during maintenances in which the CDC is kept inoperative, the operator may enable or disable this function in the voltage regulation system; When inoperative CDC situation is detected, as described above, the condition is signaled by an alarm indication in the voltage regulation system that, can also activate an output contact for remote alarm indication; The alarm indication will remain active in the voltage regulation system and the alarm contact will remain activated until the operator makes the manual alarm reset informing the voltage regulation system that he is already aware of the problem; the operator may also enable the voltage regulation system to make the inoperative CDC alarm automatic reset, the automatic reset being made as soon as a new CDC tap change attempt is successfully made.
 18. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 1 characterized by proposed voltage regulation system having the CDC Maintenance Assistant function.
 19. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 18 characterized by the CDC Maintenance Assistant function having the following features: Total CDC operation number count, since it is going into operation, by measuring the CDC position. Every time the measured tap position changes the CDC operation counter increases the number of required operations for making referred tap change (one operation in most cases, there may also be several operations in case of CDCs with intermediate positions); Partial CDC operation number count since the last inspection or maintenance made by the operator, by measuring the CDC position, in similar manner to above-described total operation number count; Initial and partial operation counters stored in the voltage regulation system non-volatile memory; initial operation numbers of both counters (total and partial) adjustable by the operator, allowing utilization of the CDC, also in old equipment, in addition to allowing operation count correction in the event of a failure in the voltage regulation system. A warning indicating that the operation number for CDC maintenance when partial operation count (since the last maintenance) has exceeded the number of operations for maintenance adjusted by the operator; with the possibility of programming an output relay for remote signaling; CDC average daily operation count, made by dividing the sum of total operation number in the last X days by the number of X days, X being a time window programmable by the operator between one and three hundred and sixty five days; Approximate Y remaining time calculation for reaching the number of operations for maintenance, according to the ratio below: $Y = \frac{\begin{matrix} {\left( {{{No}.\mspace{14mu} {of}}\mspace{14mu} {operations}\mspace{14mu} {for}\mspace{14mu} {maintenance}} \right) -} \\ \left( {{partial}\mspace{14mu} {operation}\mspace{14mu} {counter}} \right) \end{matrix}}{{Average}\mspace{14mu} {daily}\mspace{14mu} {operations}}$ Warning indication that the number of operations for CDC maintenance will be reached within Y days, when remaining time calculation for Y maintenance is lower than the number of advance days for maintenance warning adjusted by the operator between zero and three hundred and sixty five days, with the possibility of programming an output relay (6) for remote signaling; The maintenance warning indication will remain active in the voltage regulation system and the alarm contact(s) will remain activated until the operator makes a manual warning reset, informing the voltage regulation system that maintenance has already been performed. Once the reset is made, partial operation count since the last maintenance is zeroed and warnings are switched off for maintenance.
 20. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claims 18 characterized by in addition to the above-listed, the “CDC maintenance assistant”, further having the following features: Every time a CDC tap change is made, detected by tap measuring, the voltage regulation system takes a load current measurement at the time of tap change and raises it to the power of 2; obtained value is added to the already existing one in the total changed current sum recorder since the beginning of the CDC operation, which is kept in a non-volatile memory in the voltage regulation system; As described above, every time a CDC tap change is made, detected by means of tap measurement, the voltage regulation system takes the load current measurement at the time of the change and raises it to the power of 2; obtained value is also added to the already existing value in another recorder, this one dedicated to the sum of partial change current since the last CDC maintenance, which is kept in the voltage regulation system non-volatile memory; Initial values of both changed current sum records (total and partial) adjustable by the operator, allowing using the CDC maintenance assistant also in old equipment, in addition to allowing sum corrections in the event of a failure in the voltage regulation system; A warning indication that the changed current sum for CDC maintenance has been reached when the partial sum record (since the last maintenance) exceeds the sum value for maintenance adjusted by the user, with the possibility of output relay programming for remote signaling; Daily increment average calculation in the current sum changed by the CDC, made by dividing the increment in the current sum in the last W days by VV number of days, W being a time window programmable by the operator between one and three hundred and sixty five days; Approximate remaining time Z calculation for reaching sum value for maintenance, according to the formula: $Z = \frac{\left( {{Sum}\mspace{14mu} {value}\mspace{14mu} {for}\mspace{14mu} {maintenance}} \right) - \left( {{partial}\mspace{14mu} {sum}\mspace{14mu} {recorder}} \right)}{{Daily}\mspace{14mu} {increment}\mspace{14mu} {average}\mspace{14mu} {in}\mspace{14mu} {sum}}$ A warning indication that the number of operations for CDC maintenance will be reached within Z days, when remaining time for maintenance Z calculation is lower than the number of advance days for maintenance warning adjusted by user between zero and three hundred and sixty five days, having the possibility of programming the output relay for remote signaling; The maintenance warning indication remains active in the voltage regulation system and alarm contact(s) will remain activated until user makes manual warning reset, informing the voltage regulation system that maintenance has already been performed, Once this reset is made, the partial sum recorder of changed currents since the last maintenance is zeroed and maintenance warnings are switched off.
 21. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 1 characterized by proposed system performing the “smart master-commanded-individual” function.
 22. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 21 characterized by smart master-commanded-individual programming having the following features: Inhibiting the possibility of selecting any transformer as master if there is already any other transformer selected as master. In this event in which there is already a selected master, all other transformers can only be selected as commanded or individual; Inhibiting the possibility of selecting any transformer as commanded if there is not yet a transformer selected as master. In this event, in which there is not yet a selected master, all other transformers can only be selected as master or individual; Inhibiting the possibility of changing the programming of the transformer selected as master to commanded or individual if there is one or more transformers selected as commanded, in this way avoiding that there will be transformers in commanded without there being a master.
 23. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 22 characterized by in addition to what has already been commented above, the “smart master-commanded-individual programming” function having as features: Rejecting the selection change of any transformer from individual mode to commanded mode if its measured tap position is not equal to a master transformer one, avoiding thereby unnecessary alarm issuing due to tap discrepancy; If it is insisted in the attempt to program a transformer as commanded without its measured tap position being equal to a master transformer one, in addition to rejecting this programming the voltage regulation system will issue an “invalid parallelism programming” alarm, warning the operator about the situation.
 24. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 1 characterized by proposed system performing the “smart bank-individual phase programming” function.
 25. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 24 characterized by smart “bank-individual phase” programming having the following features: Inhibiting the possibility of selecting any phase of a single-phase transformer bank for operation in the “individual phase” mode if the bank is selected for operation in parallel with other banks, that is, if the bank is selected in master or commanded mode. Inhibiting the possibility of selecting any phase of a single-phase transformer bank for operation in the “individual phase” mode if the bank is selected for operation in automatic mode, that is, with CDCs being controlled according to load voltage and current measurements. Only allowing selecting one of the phases of a single-phase transformer bank for operation in “individual phase” mode if the bank is selected for operation in individual and manual mode. Automatically changing any phase of a single-phase transformer bank that is selected for operation in “individual phase” mode to “bank” mode if the bank is selected for operation in master, commanded or automatic mode.
 26. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 25 characterized by in addition to as commented above, the “smart bank-individual phase programming” having the following features: Rejecting the selection change of any phase of a transformer from “individual phase” mode to “bank” mode if its tap position is not equal to phase A one, adopted as a reference, avoiding thereby unnecessary alarm issuing due to tap discrepancy. If it is insisted in the attempt to program a phase in the “bank” mode without its tap position being equal to that of phase A, in addition to rejecting this programming the voltage regulation system will issue an “invalid parallelism programming” alarm, warning the operator about the situation.
 27. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 1 characterized by proposed system further performing the “correct synchronism and programming signaling” function.
 28. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claim 27 characterized by the “correct synchronism and programming signaling” function giving permission for closing the circuit breaker that connects the winding of each transformer in parallel with the others, allowing automating the synchronism checking function before connection in parallel. To that end, correct synchronism and programming signaling can be made through a serial communication network or further by activating an output signal for each transformer.
 29. SYSTEM FOR VOLTAGE REGULATION, CONTROL, PROTECTION AND MONITORING OF STATE OF CHANGERS UNDER POWER TRANSFORMER LOAD, VOLTAGE REGULATORS, CAPACITOR BANKS AND SIMILAR, in accordance with claims 27 characterized by the “correct synchronism and programming signaling” function having the following features: In selected transformers in individual mode no correct synchronism and programming signaling is issued, preventing transformers in this condition from being electrically connected in parallel to others (because there is no, in this case, a commitment to keep equal tap position to master transformer position); In each transformer selected in commanded mode it is signaled that synchronism and programming are correct only if transformer tap position is equal to master tap position and if current individual master-commanded situation is valid (there is only one master transformer); In selected transformer is master mode it is always signaled that synchronism and programming are correct, because tap position of this transformer as taken as a reference for selected transformers as commanded and is considered correct by default. 